- About Us
- Latest News
- Goulburn Valley Water staff excel at the Victorian Water Industry Operations Conference
- Maintenance works underway at Corop Raw Water Storage
- Work begins on new Numurkah Water Treatment Plant
- Recycling facilities established at wastewater management facilities
- Tallarook Water Main Replacement Works - Sanctuary Road
- Water pressure interruption for Dookie residents
- Water Refill Station installed at Y Water Discovery Centre – Yea Wetlands
- Euroa Secondary College wins $1,000
- Tongala Water Treatment Plant works completed
- Treated Recycled Water to be Released into the Mosquito Drain: Tatura
- Ice Pigging to clean sewer main
- Proposed Extension and Diminishment to the Broadford Sewerage District
- Proposed Extension and Diminishment to the Broadford Water District
- Nagambie clearwater storage construction to begin
- Marysville Water Treatment Plant upgrade underway
- New water treatment plant to support town growth in Numurkah
- Eildon water main replacement works
- Water main ruptures in Numurkah
- Pay your water bill securely online
- Longwood Reservoir construction works underway
- Weekend works scheduled at Tongala Water Treatment Plant
- Applications welcome for GVW customer advisory group
- Water main replacement program moves to Corio St Shepparton
- Tatura sewer jetting and root foaming to improve sewer service
- Tatura Water Tower Upgrade – Abseilers to Erect Temporary Netting
- Introduction of Stage 1 Water Restrictions for Pyalong
- Employment Opportunities
- Community Consultation
Improvement works underway at Barmah WTP
24 April 2012
Works to replace the elevated storage at the water treatment plant in Barmah are currently underway.
Goulburn Valley Water District Manager Michael McShane said that work was required due to leaks in the 25 year old tank.
“In January the elevated storage tank was taken off-line due to a leaking problem which was causing us to lose treated water,” said Mr McShane. “The tank, which is about 20m off the ground, was quite old so sections were beginning to perish, leading to leakages in a number of places.”
At this time the high lift pumps on site were adapted to ensure GVW’s Barmah customers would continue to receive treated water with no interruption. “The high lift pumps were fitted with a pressure sensor, which enabled them to sense the pressure in the water main,” he said. “This meant the water could be pumped directly into the water main, which has been an effective solution in the interim.”
This has allowed GVW to source a replacement tank which is now being installed by contractors Roe and Cook.
“The $47,000 project includes removal of the old tank and ladder, and installation of a 46kL tank, inlet pipework and access ladder.”
The works are expected to be completed by early May, when the system will return to its normal process.
For further media enquiries please contact Michaela Sargeant, 5832 0471, email@example.com.